LLRF Controller Installation
The LLRF Hardware installation was completed in July. Lab Testing of the LLRF control
software/firmware has been completed for the 4 sets of 2-cavity controllers. Network
connections and the Labview interface for all 8 HWR cavities have been tested. The LLRF
system for HWR will be tested at CMTF tomorrow morning.
#1 Updated by Philip Varghese 11 months ago
The changes for two cavity operation for HWR were made to the firmware, Labview and the frontend software.
Labview for the the 2 cavity controller did not display waveforms for Cavity B. Troubleshooting this issue
has been in progress in the development lab for the past few weeks. There were some errors in the parameter names
in Labview and the frontend software. They have all been corrected and the system is working correctly for both
Cavity A and Cavity B (controller 0 and controller 1 in Labview)