Flasher and calibration board power should normally be off, set alarm ranges accordingly, except current
The current draw should only go red when current is too high.
Power supply channel state should go yellow when channel is turned on.
[Voltage could be handled similar to current, just to prevent accidental overvoltage.]
#1 Updated by Glenn Horton-Smith over 3 years ago
- % Done changed from 0 to 100
Done. The "OnDetPower" channels 504, 505, 506, and 907 won't alarm when they're off. There will be a minor alarm if these channels come on, which an expert should acknowledge if s/he turns it on deliberately.
Note that 506 (flasher) used to have fairly narrow alarm range around about 7.5 V, and now it's possible to set it anywhere from 0 to 7.7 V without getting an alarm. That seemed to be what you were asking for, so that's what I did. Currently the voltage on 506 is set to 0 in addition to it being turned off.
504 and 505 still have tight ranges about 3.3 V for the voltage setting. They are set to 3.3 V, and I believe we always want them either off or at their correct voltage, so I left them that way.